Question about Goodman Heating & Cooling
On your t-stat you have Y, W1, W2, R, O, G, B or C or X. Y is your cooling circuit and will be the same in the air handler and heat pump unit, use the yellow wire for this circuit. W1 and W2 are your back up elec. or gas heat. Depending on how many kws or heat strips you have and t-stat wires you will put the white wire to W1 in both the t-stat and air handler. W2 is for your second stage back up heat if air handler calls for it, this will be a tan or brown or black t-stat wire and goes to W2 on t-stat and air handler. R is half of your 24v control power from the transformer and is the red wire and goes to the t-stat, air handler, and heat pump. O is for the reversing valve in the heat pump that switches it from heating and cooling. You guessed it the orange wire connect to t-stat and heat pump. G is for the blower and is the green wire to the t-stat and air handler. B or C or X is known as the common which is the other half of control circuit from 24v transform it is the blue wire and goes to the t-stat, air handler, and heat pump.
Posted on Oct 09, 2008
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Apr 05, 2016 | Goodman Heating & Cooling
Aug 22, 2015 | Heating & Cooling
Oct 14, 2012 | Goodman Heating & Cooling
Jan 03, 2011 | Goodman CLQ36AR49 Air Conditioner
Mar 18, 2010 | Goodman CKL36AR36 Air Conditioner
Jan 31, 2010 | Goodman Heating & Cooling
Oct 28, 2009 | Intertherm Heating & Cooling
Oct 27, 2009 | Heating & Cooling
Oct 16, 2009 | Goodman GMS90703BXA Heater
1,659 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: