Question about Honeywell Electronic Programmable Heat/Cool Thermostat - CT3300A100 Heater
Honeywell thermostat pro th4000 series has a slow temperature change notification. how do you account for old style anticipators.
I think I've done it - but don't take this as absolute truth.
For the Honeywell T6360B the original Potterton wiring should be rewired as follows:
Brown [Live] goes to terminal 1; Blue [neutral] goes to Terminal 2 and the yellow/green [which is not an earth but a switched live - i.e. gives live to the heating system when the thermostat clicks in] goes to terminal 3.
Obviously all done with the power isolated and when it was switched back on we had heating again :o)
It's been on over two hours now and all seems fine.
Posted on Feb 16, 2008
try holding the up and down arrow, down, at the same time, see if the time or temperature starts flashing. also the cover should lift up so you can change from heat to cool, there should be a program button or a set button to hold down. all you should have to do is adjust the time and temperature for the 4 settings during the week and the two on the weekend. should be really easy, let me know if you need some more help
Posted on Nov 13, 2008
both thermostatats will have terminal designators R,W,Y,G, possibly O/B, C, W1,W2, Y1, Y2, etc.
Simplest method is to remove wires from old stat one at a time. mark where they came from and then install at same desinated terminal on the new t-stat. Hope this helps. be sure to shut off power supply to the unit (furnace) first. The wire coming to the R (RH,RC) terminal is the 24 volt a/c hot, all others are feeding back to perform given function.
Posted on Dec 23, 2008
I don't know if this will be helpful or not, but I just installed a new Honeywell and the Honeywell customer service guy helped me get the wires done correctly. The number is 800-468-1502.
Posted on Jan 05, 2009
this thermostat does not have a deadband option, the only other thing you can do is set the program for a different temp. the cycles per hour just restrict how many times the unit comes on.
Posted on Dec 16, 2009
Tips for a great answer:
Jun 14, 2011 | Honeywell CT500 Digital Heat / Cool Manual...
Jan 20, 2011 | Honeywell Electronic Programmable...
Dec 02, 2010 | Honeywell CT500 Digital Heat / Cool Manual...
Nov 28, 2010 | Honeywell Heating & Cooling
Mar 14, 2010 | Honeywell Electronic Programmable...
Dec 15, 2009 | Coleman Heating & Cooling
Nov 18, 2009 | Honeywell Electronic Programmable...
Oct 05, 2009 | Honeywell Electronic Programmable...
Jan 11, 2009 | Honeywell Electronic Programmable...
524 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: