Question about Whirlpool LER5636P Electric Dryer
I hooked 10 gauge wires to a receptacle and wired the two hot leads to two 20 amp breakers i wired the white wire to a neutral pole inside the breaker box and the copper to a ground pole. one of the 20 amp breakers sparked and kicked off. i replaced the two breakers with a double 30 amp breaker and now i have no power to the dryer the double 30 amp breaker kicked off
I will try this again i don't think i posted it properly.
On the power cord where it connectes to the dryer make sure the red and black wire goes to the outside screws (L1& L2) the white goes in the middle and the green goes to the dryer cabinet.
If you have the red or black going to the middle one it will trip the breaker.
Posted on Nov 03, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Dec 01, 2014 | Air Tools & Compressors
Apr 15, 2014 | Whirlpool Dryers
Nov 18, 2012 | Dryers
Oct 30, 2011 | Hammering
Jan 10, 2011 | 2000 Chevrolet Silverado
Oct 30, 2010 | Electrical Supplies
Aug 19, 2010 | RELIANCE ELECTRIC WATER HEATER
May 19, 2010 | Cutler Hammer Circuit Breaker, 30 Amp 120V
Sep 27, 2009 | Dryers
Sep 12, 2009 | Maytag Dryers
69 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: