Question about LG LM-2430C2L Cool Mini Split Air Conditioner
Having air flow problems with my RUUD Silhouette II. The air flow decreases then eventually completely stops. The pipes leading from the house to the fan and compressor outside have a thick layer of ice. Water is also dripping into the pan up in the attic. Is there an LED fault/trouble indicator on the Silhoette II? Any ideas what is causing the trouble?
You will need to let the indoor fan run for several hours to defrost the indoor coil. it may take 12 hours to defrost you'll know when it's clear when the vents are blowing like usual again. Then run the unit for 5 minuits and check the large copper insulated line going to the outdoor unit. is it cold? if not you need a refrigerant charge. If it is then make sure never to run the unit below 70 degrees and check your air fliter and return duct for blockage of possible collapse. Also you may have a dirty indoor coil chac that and clean the outdoor one as well.
Posted on Jul 27, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Feb 02, 2011 | Ruud UBHC Air Conditioner
Dec 11, 2010 | Ruud Heating & Cooling
May 13, 2010 | Ruud UBHC Air Conditioner
Mar 22, 2010 | Ruud UBHC Air Conditioner
Jul 23, 2009 | Heating & Cooling
Mar 15, 2009 | Ruud UBHC Air Conditioner
Jan 13, 2009 | Heating & Cooling
328 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: