Question about Heating & Cooling
The pressure in our boiler is slightly high (should be 1-1.5 and it is around 2-2.5) - it is only 2 years old and we have had someone in to look at it recently as the thermostat was not behaving correctly - so I am confident there is not anything wrong with it - but now that we are starting to use the heat again, the pressure rises up into the 'red' area (3-4) when the heat is turned on. Is this something to be worried about? And is there anything that we can do to release the pressure?
Thanks for any assistance!
My heat line capriz 25 boiler is flashing that i have flam or gas falure and has stoped workin? what do i do?
Posted on Feb 11, 2009
You should have a filling loop built in to the boiler or external make shaw this is not letting water in to the system, also being a sealed system hot water will expand. so on your boiler you will have a expansion vessel which has to be filled with air so that the water can expand in to it. undo the valve which will be like a tyre valve off a car and quickly press the pin if u get air spay out with quite alot of pressure u should be ok. if empty you need to top it up to the manufactures instructions normaly about 1 bar. if both the above are ok the expansion vessle is broken
Posted on Sep 12, 2009
Crack open any joint in the system like a joint to a radiator and let a little water drip out. you should not use when in the red
Posted on Oct 05, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jun 19, 2014 | Heating & Cooling
Sep 30, 2010 | Microwave Ovens
May 31, 2010 | Isomac Tea Espresso Machine
Feb 07, 2010 | Desa International CBN30T Central Heating...
Mar 27, 2009 | Water Heaters
Mar 02, 2009 | Water Heaters
Feb 05, 2009 | Combi Centre DX - Mango
Jan 22, 2009 | Protech Systems FasNSeal FSWMKE4 4" Vent...
Jul 19, 2017 | Heating & Cooling
1,505 people viewed this question
Usually answered in minutes!