Question about Goodman CLQ36AR49 Air Conditioner
It's probably too late to recommend capturing (bottling) the charge in the condensing unit...... With that said the absolute 100% way to charge any unit is to use the weight method. If you look on the nameplate of the unit it will provide you the amount of refrigerant needed in lbs and ounces, the manufacture instruction manual will give you the additional weight needed for the lenght of the line set. In the event you don't have the ability to weigh the refrigerant accurately you can always wrap the condensing unit with a blanket reduce the condensing capacity of the condenser this will simulate a warmer ambient and allow you to charge the unit. If the unit has a fixed orfice metering device you can use the superheat method, if the unit has a TXV (thermal expansioin valve) you should use the subcooling method. Either of these methods with detailed proceedures can be found on any of the popular search engines. Hope this helps and good luck!
Posted on Oct 05, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Feb 20, 2015 | Heating & Cooling
Jan 30, 2014 | Heating & Cooling
Aug 17, 2012 | Weather King 12AJA6001AH Air Conditioner
Jun 10, 2011 | Heating & Cooling
Jul 21, 2009 | Weather King 10AJA3001AH Air Conditioner
Jul 17, 2009 | Freezers
Jun 07, 2009 | Weather King 12AJA4801AH Air Conditioner
Oct 05, 2008 | Goodman CLQ36AR49 Air Conditioner
Jul 07, 2008 | DeLonghi Heating & Cooling
Jun 10, 2008 | Weather King 10AJA3601AH Air Conditioner
42 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: