Question about Goodman GMS90703BXA Heater
The venter blower, igniter, gas, flame all go on as they should. Then about 5 sec. after the igniter turns off the gas shuts off. I changed the flame sensor thinking that was the problem, but still the same. Any advice welcomed
Clean the sensor with a piece of fine sand paper. It gets a coating on it after a few years of service. I had my cleaned for $160, it took five minutes.
Posted on Feb 03, 2009
Check the pressure sensor. I tapped on mine a few times, removed the hose and checked it for blockage and replaced. It has been working fine since. I do have a new sensor on order.
Posted on Oct 22, 2008
Make sure you trace the wire to the flame sensor back to the board and see that it is still connected.
Posted on Oct 11, 2008
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Oct 22, 2013 | Goodman GMS90703BXA Heater
Oct 05, 2012 | Goodman Manufacturing Goodman GMH950704CX...
Dec 03, 2010 | Goodman GMS80903BNA Heater
Nov 13, 2010 | Goodman Heating & Cooling
Jan 26, 2010 | Goodman Heating & Cooling
Dec 29, 2009 | Goodman Heating & Cooling
Dec 16, 2009 | Goodman GMS90703BXA Heater
Feb 15, 2009 | Goodman GMS90703BXA Heater
Feb 08, 2009 | Goodman GDS80904BNA Open Flame Heater
Nov 05, 2008 | Goodman GMS90703BXA Heater
825 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: