Question about Rinnai Unvented Gas Zone Heater. 99% fuel efficient: Blower with Thermostat
Heater is not much over 1 yr old moved to new location for this heating season after hook up will not start combustion erroe code 31
can i fix it or do i have to send it some where
Check out this link for more detailed help
Check for restrictions in air flow around unit and vent terminal.
Check sensor wiring for damage.
Measure resistance of sensor.
Clean sensor of scale build up.
Ensure fan blade is tight on motor shaft and is in good condition
Ensure fan will turn freely.
Check wiring harness to motor for damaged and/or loose connections.
Measure resistance of motor winding.
To display the most recent error codes press and hold the “On/Off” button for 2 seconds. While holding the “On/Off” button press the button. The last 9 error codes will flash one after the other. To exit this mode press the“On/Off” and button as before.
To display the water flow through the water heater press and hold the button for 2 seconds and withoutreleasing the button press the “On/Off” button.
To display the outlet water temperature press and hold the button for 2 seconds and without releasing the
button press the “On/Off” button.
Flushing the Heat Exchange (Error Code: LC or 00)
An “LC” or “00” error code indicates the unit is beginning to lime up and must be flushed. Failure to flush the
appliance will cause damage to the heat exchanger. Damage caused by lime buildup is not covered by the unit’s
warranty. After flushing, reset the LC fault code by turning off the power to the unit and turning the power back on
1. Disconnect electrical power to the water heater.
2. Close the shutoff valves on both the hot water and cold
water lines (V3 and V4).
3. Connect pump outlet hose (H1) to the cold water line at
service valve (V2).
4. Connect drain hose (H3) to service valve (V1).
5. Pour approximately 4 gallons of virgin, food grade, white
vinegar or citric acid into pail.
6. Place the drain hose (H3) and the hose (H2) to the pump
inlet into the cleaning solution.
7. Open both service valves (V1 and V2) on the hot water and
cold water lines.
8. Operate the pump and allow the cleaning solution to
circulate through the water heater for at least 45 minutes.
9. Turn off the pump.
10. Rinse the cleaning solution from the water heater as follows:
a. remove the free end of the drain hose (H3) from the pail
b. close service valve, (V2), and open shutoff valve, (V4).
Do not open shutoff valve, (V3).
c. allow water to flow through the water heater for 5 minutes
d. close service valve, (V1), and open shutoff valve, (V3).
11. Disconnect all hoses.
12. Remove the in-line filter at the cold water inlet and clean out
any residue. Place filter back into unit.
13. Restore electrical power to the water heater.
Posted on Oct 06, 2008
while placing it to another location. did it get hit by someone... check in this respect by the way
dont rate it until u satisfy with it or it helps!
Posted on Oct 06, 2008
You will probably need to get it serviced. First check if the wall socket is working properly and the power cord and plug is in good condition.
You can find a repair service near you by entering your zip in the box to the right that says "Repair Service". Just mention that you were referred by Fixya, and you may just get a discount :)
Hope that helps!
Please don’t forget to rate or "Accept" the solution if it helped you in any way, or leads you to a fix.
Thank you for using FixYa!
Posted on Oct 04, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Apr 06, 2013 | Desa International Unvented Gas Space...
Nov 06, 2010 | Rinnai Unvented Gas Zone Heater. 99% fuel...
Oct 09, 2009 | Rinnai Unvented Gas Zone Heater. 99% fuel...
Jul 07, 2009 | Rinnai RHFE-1004FA 38,400 BTU Energy Saver...
Dec 11, 2008 | Rinnai Unvented Gas Zone Heater. 99% fuel...
Nov 23, 2008 | Rinnai Unvented Gas Zone Heater. 99% fuel...
Oct 04, 2008 | Rinnai Unvented Gas Zone Heater. 99% fuel...
Aug 13, 2007 | Rinnai Unvented Gas Zone Heater. 99% fuel...
Jan 08, 2007 | Rinnai Unvented Gas Zone Heater. 99% fuel...
Dec 12, 2013 | Rinnai Unvented Gas Zone Heater. 99% fuel...
198 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: