Question about Heating & Cooling
The actual final solution was to replace the fuel valve/solenoid following which the boiler has run without failure.
The conclusion was that the fuel valve solenoid was ok when cold but when heated up had some sort of electrical breakdown in its coils, causing the fuel valve to fluctuate until the boiler locked out.
Posted on Oct 17, 2008
You could have a problem with a temperature sensor.
it would not be the flame sensor since it could not wait 6 mins to sense that there is flame in the unit.
could be a temperature sensor problem where it is sensing a temperature which could be correct but it is sending a wrong signal to the controller to turn off the flame and start another cycle.
tnx 4 using fixya,
Posted on Oct 04, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Dec 21, 2015 | Ovens
Oct 23, 2014 | Heating & Cooling
Jan 05, 2011 | Heating & Cooling
Nov 27, 2010 | Heating & Cooling
May 01, 2010 | 1999 Pontiac Grand Am GT
Jun 08, 2009 | Heating & Cooling
Jan 19, 2009 | Water Heaters
Dec 15, 2008 | Heating & Cooling
353 people viewed this question
Usually answered in minutes!