Question about Air Conditioners
The actual final solution was to replace the fuel valve/solenoid following which the boiler has run without failure.
The conclusion was that the fuel valve solenoid was ok when cold but when heated up had some sort of electrical breakdown in its coils, causing the fuel valve to fluctuate until the boiler locked out.
Posted on Oct 17, 2008
You could have a problem with a temperature sensor.
it would not be the flame sensor since it could not wait 6 mins to sense that there is flame in the unit.
could be a temperature sensor problem where it is sensing a temperature which could be correct but it is sending a wrong signal to the controller to turn off the flame and start another cycle.
tnx 4 using fixya,
Posted on Oct 04, 2008
Tips for a great answer:
Nov 23, 2013 | Air Conditioners
Here is a tip I wrote about how you can bleed the air out of the lines to get the oil burner working again...
How to Bleed Oil Burner - Beckett Oil Burner Repair
Apr 27, 2011 | Air Conditioners
Apr 09, 2011 | Air Conditioners
Jan 05, 2011 | Air Conditioners
Nov 27, 2010 | Air Conditioners
Sep 05, 2010 | Air Conditioners
Dec 15, 2008 | Air Conditioners
Oct 31, 2008 | Air Conditioners
352 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: