Question about Amana Heating & Cooling
Pressure switch open. Remove the small hose at the blower assy and gently **** on it. You should hear the switch on the other end of that hose change states. If not then it's the hose (cheap) or the switch (100 bucks but tough to find 2 years ago) or the wiring to/from or the control module. If it does do you have a bunch of white **** (the gasket) coming out of the black blower mount? I had to remove broken gasket and Permatex the seal to create the proper pressure; that's probably your problem as well.
Posted on Oct 03, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jul 13, 2016 | Heating & Cooling
Nov 21, 2015 | Heating & Cooling
Jan 31, 2011 | Heating & Cooling
Jan 26, 2011 | Heating & Cooling
Aug 10, 2010 | Heating & Cooling
Dec 31, 2009 | Heating & Cooling
Nov 28, 2009 | Heating & Cooling
Nov 15, 2008 | Amana Heating & Cooling
554 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: