Question about Carrier 38CKC042 Air Conditioner
What you have is a 24v control circuit problem. There is a transformer in the air handler ( inside unit ) you will have 220v on the one side and 24v on the other. If you have 24v from transform there is a small fuse on the pc board that could blow during power problems. On the inside cover you should find a wiring diagram.
Posted on Oct 01, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Aug 10, 2016 | Honeywell TH5110D1006 Focus PRO 5000...
Dec 02, 2014 | Hotpoint RGB745 Gas Kitchen Range
Jan 12, 2011 | Sharp AR-5316 Advanced Digital Imager...
Here is the reason for that problem per the manufaturers web-site
The low-pressure switch senses the refrigerant pressure in the sealed refrigeration system to
protect against certain conditions that could be detrimental to compressor life. The switch shuts
the unit down in the event of loss of refrigerant, fan motor failure, evaporator freeze-up and
airflow blockage. The switch automatically resets when the pressure rises to normal operating
pressures. The display will show "LP" if this switch is tripped.
The low-pressure switch will shut the heat pump down when the evaporator starts to freeze.
When the unit starts to freeze the low-pressure switch will be tripped, causing the display to read
"LP" This will prevent the evaporator from becoming damaged or deformed.
If the air outside the heat pump is not warm enough to produce heat, the system will shut down.
The actual point at which your unit will shut down due to low temperature varies depending on
which model you purchased, current weather conditions, and the amount of sunlight reaching the
heat pump. The shutdown can occur anywhere within a wide range of temperatures, usually 45°F-
55°F. This is not a "fixed" range. We stress that climate conditions, sunlight, and various models
respond quite differently to low ambient temperature. A shutdown occurs because low
temperatures will activate the systems low-pressure safeguard switch (digital thermostats will
display a code "LP".) The unit will start up again when the temperature has raised enough to reset
this switch. Note: Low ambient temperature does not necessarily affect the Chiller models
or the cooling cycle of the heat/cool units.
If this post has helped you, please take the time to vote positively for me on this site. If you need additional help, I can be reached @: email@example.com
Oct 23, 2010 | Hayward Heatpro 81k Btu Swimming Pool Heat...
Nov 26, 2009 | KitchenAid KEBS177 Electric Single Oven
Jul 06, 2009 | Cyberhome DVR 1600 DVD Recorder
Jun 18, 2009 | Frigidaire Affinity ATF7000ES Front Load...
Oct 01, 2008 | Air Tools & Compressors
Sep 30, 2008 | Carrier 38CKC036 Air Conditioner
May 17, 2008 | Canon PowerShot A700 Digital Camera
208 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: