Question about Carrier 38CKC042 Air Conditioner
What you have is a 24v control circuit problem. There is a transformer in the air handler ( inside unit ) you will have 220v on the one side and 24v on the other. If you have 24v from transform there is a small fuse on the pc board that could blow during power problems. On the inside cover you should find a wiring diagram.
Posted on Oct 01, 2008
Tips for a great answer:
Dec 05, 2013 | Coleman Mach 15 Air Conditioner
Nov 08, 2013 | Ruud UBHC Air Conditioner
Nov 03, 2013 | Air Conditioners
Jul 16, 2011 | Air Conditioners
Feb 26, 2010 | Samsung AP500PF Air Conditioner
Aug 21, 2009 | Air Conditioners
Sep 30, 2008 | Carrier 38CKC036 Air Conditioner
Dec 06, 2007 | Air Conditioners
207 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: