Question about Goodman GDS80904BNA Open Flame Heater
My Goodman furnace is less than 3 years old. Occasionally, not always, but now with increased frequency, My furnace will fail ignition and go into the one hour sit and reset mode. The exhaust fan comes on, ignition stick starts glowing, I here a click, then the glow stick goes out. The furnace will not fire. After three attempts, it goes into lockout state for one hour. There is no obstruction in the exhaust stack, and I have a 6" air inlet duct that stops 18" off the floor bringing in fresh air from the attic air space into the furnace room. The attic air is cool, and the inlet pipe is relatively near a gable vent to bring in outside combustible air. The inlet duct is approximately 30" from furnace. Any help will be greatly appreciated. Thanks
If your igniter comes on but no ignition, that eliminates the possibility of a bad or clogged pressure switch, high limit or flame rollout switch. Sounds to me like you have a control board, or a gas valve going bad. Could even be some loose, corroded, or faulty wiring. Before the igniter comes on the furnace does a self diagnostics to ensure everything is working, or the furnace will not make it to the igniter sequence. Inducer motor, pressure switch/s, limit controls are closed…then comes on the ignitier, gas valve opens, pilot runners and burners ignite, flame sensor detects the flame, blower comes on and all operations are working.
Hope this helps
Posted on Dec 02, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Dec 17, 2014 | Goodman Manufacturing...
Nov 04, 2012 | Goodman Heating & Cooling
Nov 23, 2011 | Goodman Heating & Cooling
Jul 21, 2011 | Goodman GMS90703BXA Heater
Jan 18, 2010 | Goodman GMS80903BNA Heater
Dec 12, 2009 | Heating & Cooling
Oct 07, 2009 | Goodman GMS90703BXA Heater
Jan 10, 2009 | Goodman GDS81155CNA Open Flame Mid-Size...
762 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: