Question about Heating & Cooling
I had to install a new thermostat, I bought the Honeywell RTH7500, I have a multi stage heat pump. When I activate the thermostat for cool air, the fan will come on but no cool air, I can get the heat to work, but no A/C. Any suggestions?
Assumed all the wiring are correct,
to change from manual switching from heat to cool, press [system] button ( left ) to go into system setting.
then press and hold the [fan] middle button untill option display 120
use up down button to select option 300 ( Manual/Autochangeover) ,
select 0 for manual, 1 for automatic. ( read caution in page 22 of installation manual )
Posted on Oct 14, 2008
You the man!
I had an old Baystat 239 that would never shut off. I bought the Honeywell RTH7500, couldn't get it to cool, found your solution online and moments later I had cool temps! Thanks for the help!
Posted on Jun 07, 2010
The thermostat must be programmed (setup) for operation with your system. Check the manual for the settings for use with a multistage heat pump. If you are running a dual fuel system then be sure you also include this when you do your set up. In addition you must also set up the thermostat so that it will operate in the auto-change over mode.
Posted on Sep 30, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Nov 18, 2015 | Honeywell Heating & Cooling
Mar 21, 2013 | Heating & Cooling
Apr 17, 2010 | Honeywell Programmable Thermostat Heater
Apr 02, 2010 | Honeywell Electronic Programmable...
May 10, 2009 | Heating & Cooling
Jan 17, 2009 | Honeywell Programmable Thermostat Heater
Nov 24, 2008 | Honeywell Electronic Programmable...
Aug 11, 2008 | Honeywell Programmable Thermostat Heater
2,826 people viewed this question
Usually answered in minutes!