Question about Carrier 38BRC048 Air Conditioner
I'm currently experiencing an intermittent problem with my Carrier A/C Model FC4BNF042. It shuts down completely and fails to restart. When in this condition, there is no LCD display on the thermostat indicating the unit is on. I've also checked but was unable to detect 24V from the output side of the transformer although the 220V input was fine. I isolated the transformer, thinking it may be bad, and performed a simple resistance check. The primary side read 74 ohms and the secondary 1.7 ohms. Even though it appeared a little high I assumed the transformer was okay since it did not have an obvious short or open coil. I proceeded to visually check all the wiring, components, fuses, etc. and all appeared to be fine in the air handler unit. I have a gut feeling the thermostat may be defective. Is there something that I may be overlooking and could check before I go out to and buy a new thermostat? By the way, the unit began working again about an hour after I last checked it.
It sounds like there is something in the system that is over heating. A t-stat will either work or it won't there are relays that have 24v coils and can become weak. If your air handler is shutting down it shut down the condenser, if the air handler is staying on but condenser is shuting down check the outside contactor. I am an a/c contractor and can be contacted at 504-722-3946 Eddie.
Posted on Sep 29, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Dec 24, 2014 | Carrier Heating & Cooling
Jan 07, 2011 | Heating & Cooling
Sep 22, 2010 | Heating & Cooling
Oct 30, 2009 | Carrier XHB123D X/Y Series Heat/Cool Air...
Aug 11, 2009 | Carrier 38CKC042 Air Conditioner
Apr 23, 2009 | Intertherm P3RA-048K Air Conditioner
Mar 11, 2009 | Carrier Heating & Cooling
Feb 15, 2009 | Carrier XHB123D X/Y Series Heat/Cool Air...
Dec 06, 2008 | Carrier XHB123D X/Y Series Heat/Cool Air...
May 28, 2014 | Carrier 38BRC048 Air Conditioner
285 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: