Question about Plumbing
Can I wrap the power cable around my discharge pipe without damaging of over heating th cable or discharge pipe. I have 20 foot cable and the receptacle is only ten feet away. I am concerned that the excess cable could be a safety issue but I am also concerned with the SJTW cable rating and heat dissapation
What motor's amp draw? What is the pipe material? If you can loop the wire back and forth and tie it to the discharge pipe with a wire tie you would be better off. I have seen a 110 volt electric smoker melt the power cord in a retractable shop light. A coil of romex without metal at the center will do the same thing.
Posted on Oct 08, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Sep 08, 2011 | Flotec Corrosion Resistant Shallow Well...
Aug 16, 2011 | Flotec Corrosion Resistant Shallow Well...
Thank you for posting your question here on Fixya.com.
The orientation for a sump pump/check valve are the pump is in the bottom of the pit, the discharge pipe leads up into a check valve, usually very close to if not threaded into the pump discharge, and then the pipe continues up and out to wherever your water discharges to. The weep hole needs to be below the check valve.
The hole is there to prevent an air lock in the pump which would prevent it from moving water.
If the water trapped in the vertical run of the discharge pipe is returning to the pit once the pump shuts off the problem is the check valve is not holding or the hole is on the wrong side of the flapper assembly. Did the check valve come with the unit? If not, you will need to fix it if you can or replace it.
If this answer does not fix your problem, please comment with additional details prior to rating the answer. You may also contact me thru our website at www.arrowpools.net. Positive feedback is appreciated once your problem is solved!
Feb 23, 2011 | Flotec SimerOmni 3986 SS Sump Pump
Nov 04, 2010 | AO Smith 1 1/2 HP 115/230V 56C Replacement...
Oct 06, 2010 | Do It Best Column Sump Pump
Dec 10, 2009 | Plumbing
Oct 24, 2009 | Plumbing
Sep 27, 2009 | Plumbing
Aug 25, 2009 | Plumbing
Aug 19, 2009 | Plumbing
149 people viewed this question
Usually answered in minutes!