Question about Coleman Heating & Cooling
This could be a couple of things, first is the fan limit switch. Make sure your fan limit is set at the correct settings, there is a fan on setting and a flame shut off setting located on the front of air handler inside the front cover. Usaully set at 140 fan on 200 gas shut off. You do not say what unit you have so this could be a pc board or module. Second this could be the blower it's self over heating and shutting down, feel if motor is gettig hot. This could be a run cap. or motor it's self. But it is more than likely the limit switch.
Posted on Sep 29, 2008
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Sep 10, 2017 | Heating & Cooling
Apr 03, 2011 | Goodman Heating & Cooling
Nov 25, 2010 | Heating & Cooling
Oct 29, 2010 | Electric Circuit Breaker Kit for Furnace
Mar 25, 2010 | Heating & Cooling
Jan 31, 2010 | Goodman GMS90703BXA Heater
Mar 02, 2009 | Goodman GMS90703BXA Heater
Feb 06, 2009 | Carrier Heating & Cooling
Nov 25, 2007 | Heating & Cooling
Dec 10, 2017 | Coleman Heating & Cooling
49 people viewed this question
Usually answered in minutes!