Question about Intertherm P3RA-048K Air Conditioner
Outside unit on but inside not blowing air
If it's not blowing cold air it could be for these reason...
1... it has a low charge. generally if the high pressure switch in the unit detects a low charge it will shut the compressor down to prevent it from seizing up.
2 you have a leak...once again the sensor in the system will shut down.
3 debrie across the condensor... you have to have airflow over the coils and fins of the condensor to disapate the heat thus providing the cool air that the fan blows.
4 the thermostic sensor is bad. this is responsible for the adjustment of how and when the compressor runs.
Unfortunately because a/c units for residentual and commercial use a freon based refrigerant you have to be liscense to repair the units. so my suggestion is to contact a certified HVAC technician to work on your unit
please rate this........thanks
Posted on Sep 29, 2008
Not familliar w u unit, but ref is a redundant operation. the inside blower (fan) is not running but mabe it is? and cant move air because the coil is blocked (debris dust)?.someone will dissasemble (expose) u indoor unit and that where troubleshooting begins. that takes a little mechanical knowledge n if u have what it takes?, than google the mfr & model # to obtain a service manual. all u answers lie whithin such manual.
Posted on Sep 28, 2008
Clicking sound is the contactor engaging to start the outside unit. Check for a burnt off wire at the contactor. For some reason you are not getting power to the outside unit. If you find a burnt off wire shut off all power to it then remake the connection at the point of the circuit break.
Posted on Jun 27, 2008
The capacitor is located inside the control panel on the outside unit. It is round or oval and silver in color.It runs the outdoor fan and the compressor both.
The terminals are marked= C, /F or fan/, H or herm. C-F-H.
The microfarad rating is printed on the capacitor. Make a color code wire diagram before removeing wires.
Disconnect power to the unit. Use a insulated screwdriver to short out the terminals on the capacitor before removing it.
Posted on Apr 27, 2009
It sounds like you have a unit called a heat pump. When a heat pump unit is in cooling mode the outside unit blows hot air and the inside unit blows cold air. If the outside unit is blowing cold then the indoor unit is most likely blowing room temperature or warm air. It sounds like the thermostat could be controlling incorrectly or you could have a failed reversing valve which is the device that switches the unit from heating to cooling mode.
Posted on Jun 02, 2009
SOURCE: central air blowing warm air
2 things could be happening. 1, inside unit needs filter changed and coil cleaned. 2, unit is low on freon. A/C tech should be able to check for both. You can check the a/c coil to clean it yourself but to check for low freon this will have to be done by a a/c tech due to the complexity of the system. the ice is caused by a series of things however, check the a/c filter and the coil located behind the filter. this coil should be free of any debris. if you have indoor pets sometimes the hair clogs the coil causing the freeze up.. To clean the coil you need to get a small weed killing sprayer.. At the a/c supply house you can purchase cleaning solution that is easy to use an safe for the enviroment also leaves your house smelling great. if the coil inside has been cleaned check to see if the coil outside is clean if not you can clean it with a water hose by spraying the coils out. MAKE SURE TO KILL THE POWER beforehand. Also spry the water onto the coils only and spray in the oppisite direction of air flow. Have system checked by a/c tech if you do not feel comfortable doing any of these suggestions
Posted on Jul 16, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Nov 05, 2014 | Heating & Cooling
Jun 02, 2014 | Ruud Central System Air Conditioner
May 13, 2014 | Goodman CKL36AR36 Air Conditioner
Jul 29, 2011 | Heating & Cooling
Jul 08, 2010 | Ruud UAPA042 Air Conditioner
Aug 09, 2009 | Carrier Heating & Cooling
Jun 19, 2009 | Ecoquest Flair Air Purifier
128 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: