Question about Hunter Heating & Cooling
The standard code is red is power or [R] on your t-stat, yellow is cooling or [Y], blue is common or [C], and green is fan or [G]. This is standard across U.S.A. if the installer, installed it correctly. I as a rule of thumb look in the air handler to make sure the colors are correct. I always tell my techs. that elec. doesn't any color and this could you from burning up your t-stat. Plus, while your in the a/h you can make sure your blue common wire is connected. You will need this to run your programmable t-stat. If you are replacing a reg. t-stat then it might not be in use, but without it your running the t-stat on battery back up.
Posted on Sep 28, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jun 12, 2011 | Heating & Cooling
May 28, 2011 | Hunter Fan Company 5/1/1 Programmable...
May 23, 2011 | Heating & Cooling
Nov 10, 2010 | Hunter Heating & Cooling
Aug 21, 2009 | Hunter Fan Company 5/1/1 Programmable...
Jun 16, 2009 | Hunter Fan Company 5/1/1 Programmable...
Mar 08, 2009 | Hunter Fan Company 5/1/1 Programmable...
Jan 12, 2009 | Hunter Fan Company 5/1/1 Programmable...
Dec 11, 2008 | Goodman CLQ36AR49 Air Conditioner
Jan 08, 2017 | Hunter Heating & Cooling
71 people viewed this question
Usually answered in minutes!