Question about Heating & Cooling
An a/c coil freezes up because there is no heat load on the coil. It's either dirty, low on refrigerant, filter dirty, the fan is not running. Defrost the coil by leaving the unit off until defrosted. If the coil is accessible you use a coil cleaner thru a chemical sprayer and spray coil. Do not use the stuff they sell at Home Depot or Lowe's they don't work. get some from an a/c contractor or supply house. After with the chemical sprayer rinse the coil with water. You may have to repeat a couple of time to get it good and clean. If you can not access the coils then you will need to pull and clean the coils. To do this you'll need to pump down the refrigerant into the condenser coil and cut the evap. coil out of the system clean and reinstall. With this you'll need refrigerant gauges and know how to solder and have access to refrigerant. The same if your low on refrigerant you,ll need access to gauges and refrigerant. Depending on system it's either R-22 or R-410 refrigerant.
Posted on Sep 27, 2008
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jun 27, 2015 | Heating & Cooling
Jan 04, 2015 | Dehumidifiers
Aug 16, 2011 | GE GSS25SGMBS Side by Side Refrigerator
Aug 05, 2011 | Haier ESA3109 WallWindow Air Conditioner
Oct 30, 2010 | Home
Aug 25, 2010 | Honeywell Heating & Cooling
Jun 06, 2010 | Frigidaire Heating & Cooling
Jun 03, 2010 | Whirlpool ACC108PS Air Conditioner
Apr 29, 2009 | Kenmore Refrigerators
393 people viewed this question
Usually answered in minutes!