Question about Heating & Cooling
SOURCE: Gas boiler won't stay lit!
The burners and pilot need to be cleaned.
Turn off gas and power, remove the burners and pilot. Clean with a brass wire brush. (Steel wire can be used but very carefully) Remove all rust dirt etc. reinstall and it should fire right up.
Posted on Dec 29, 2008
SOURCE: I have an Ideal Classic
The solenoid is not opening the gas valve so you need to replace the gas valve, as for price I have no Idea...
But please remember to get a GAS SAFE REGISTERED engineer to carry out this simple replacement...
Posted on Jan 20, 2010
SOURCE: I have a sv9500m 2674
Hello,If you cleaned the flame sensor and it is in the pilot flame,Try adding a ground wire from the pilot assembly to any close screw to boost the (pilot on) signal.Also if the valve has been sitting for a while give a tap once during (pilot on) to make sure the diaphram is just not hung up.I would hate to replace the valve and still have the same problem.
Posted on Oct 15, 2010
Tips for a great answer:
Oct 22, 2014 | Water Heaters
Apr 07, 2014 | Water Heaters
Dec 23, 2013 | Heating & Cooling
Dec 17, 2013 | Carrier Weathermaker 8000 Gas Furnace 125k...
Nov 24, 2013 | Heating & Cooling
Nov 18, 2013 | Honeywell Furnace Gas Valve Sv9501h2409
Dec 14, 2008 | Water Heaters
Feb 29, 2008 | GPS
188 people viewed this question
Usually answered in minutes!