Question about Gb Electrical 100 Amp GE Load Center
HOW DO YOU REPLACE A MAIN CIRCUIT BREAKER IN THE BREAKER BOX OF A HOME?
I would tend to agree with "Tripleauto". If you do not disconnect the electrical supply to the house, you run the risk of having 240 volts at up to about 75 KVA coursing through your body. Needless to say, before the transformer blows out or someone cuts off the power, your corpse will be mostly ash. Call the power company to co-ordinate having the power turned off while you or your electrician do the work. Once the power is off, swapping out the main breaker is a relatively simple job, assuming you can find an exact replacement. If there is no exact replacement, as in the panel is fairly old and the breaker is no longer available, you will end up having to replace the whole panel or add a 125 amp breaker in a separate enclosure in an accessible location between the meter socket and the breaker box, preferably within reach of the breaker panel. The International Residential Code requires a disconnct where there are more than six breakers needed to turn off all power to the dwelling. Check with your local Building Code office before doing anything.
--Peter Nomikos, International Code Council Master Code Professional
Building and Zoning Director, City of Mauldin, SC
Posted on Feb 26, 2009
I dont mean this to sound arrogant. but if you have to ask you might be best to have a professional to do it. the wires coming into the box will be hot without being able to pull meter off of house to disconnect. the panel has to come off and many are different
Posted on Sep 29, 2008
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Nov 22, 2012 | Heating & Cooling
Oct 27, 2012 | Electrical Supplies
Oct 20, 2012 | Square D Qo 125 Amp 24 Circuit Indoor...
Aug 22, 2011 | Connecticut Electric UBIF040N FPE...
Feb 14, 2011 | Cutler Hammer "WESTINGHOUSE" MAIN DOUBLE...
Jan 24, 2010 | Cutler Hammer 125 Amp Main Lug Indoor Load...
Jul 14, 2009 | Siemens /ITE 100Amp 2-pole molded circuit...
Mar 06, 2009 | Connecticut Electric & SWITCH UBIP130...
Dec 31, 2008 | Siemens /ITE 100Amp 3-pole molded circuit...
3,109 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: