Question about Heating & Cooling
Try using a jumper wire between w and red on the stat subbase. that will take the stat out of the equation , if it has a bad heat anticipator etc. if furnace fires every time and stays on stat is the problem be sure glow ignitor is positioned in the flame after lighting as it proofs flame on some models . also look for a needle like sensor sticking into the flame on some it also proofs flame. you can gently remove and clean with sand cloth and theyll work sometimes but best to replace if to coroded.
Posted on Oct 10, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Feb 03, 2016 | American Standard Heating & Cooling
Mar 06, 2015 | American Standard 5000 Heat Pump Unit
Jan 26, 2013 | American Standard Trane Ge Gas Furnace...
Aug 28, 2011 | American Standard Heating & Cooling
Jun 28, 2011 | American Standard Heating & Cooling
Oct 29, 2010 | American Standard Heating & Cooling
Feb 23, 2010 | Heating & Cooling
Oct 27, 2009 | Heating & Cooling
Jun 24, 2009 | Heating & Cooling
Jan 22, 2017 | Slant Fin Heating & Cooling
80 people viewed this question
Usually answered in minutes!