Question about Air Conditioners
Try using a jumper wire between w and red on the stat subbase. that will take the stat out of the equation , if it has a bad heat anticipator etc. if furnace fires every time and stays on stat is the problem be sure glow ignitor is positioned in the flame after lighting as it proofs flame on some models . also look for a needle like sensor sticking into the flame on some it also proofs flame. you can gently remove and clean with sand cloth and theyll work sometimes but best to replace if to coroded.
Posted on Oct 10, 2008
Tips for a great answer:
Feb 03, 2016 | American Standard Air Conditioners
Mar 06, 2015 | American Standard 5000 Heat Pump Unit
Jan 26, 2013 | American Standard Trane Ge Gas Furnace...
Aug 28, 2011 | American Standard Air Conditioners
Jun 28, 2011 | American Standard Air Conditioners
Oct 29, 2010 | American Standard Air Conditioners
Feb 23, 2010 | Air Conditioners
Oct 27, 2009 | Air Conditioners
Jun 24, 2009 | Air Conditioners
80 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: