Question about Intertherm Heating & Cooling
My control board burned out and I replaced it. My furnace and ac still remain inop-I also replaced the thermostat with a known good one and I wired the new board exactly like my old one was wired. If I go out to the compressor and push the contactor on manually to start the unit, the fan runs but I cant tell if the compressor is kicking on or not. My lines dont get cold and heat will blow from the vents. Also the only way my blower comes on is if I turn it on at the switch. I have spoken to the parts place and they believe I may have had a lightning strike on the ground near my house and that may have caused the board to burn out. What else should I check and where can I get a diagram for my intertherm unit. It is a 1995 year model and the number on the furnace unit is E1EH-815HA.
To see if it is the t-stat or the system you can unwire the entire t-stat and jump out the wires. never touch the blue to any other wire or you will blow the low voltage fuse on new board. if you jump red to yellow and your condensing unit cycles on the t-stat is wired wrong or wrong style. If not go check the yellow wire at cond. unit and see if power is even going to it.
Posted on Sep 24, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Aug 18, 2014 | Heating & Cooling
Jul 04, 2014 | Computers & Internet
Jun 05, 2013 | Coleman Home Electric Furnace Eb15b/Eb15d
Dec 19, 2012 | Heating & Cooling
Feb 01, 2011 | Heating & Cooling
Sep 12, 2009 | Heating & Cooling
May 04, 2009 | Heating & Cooling
Apr 16, 2009 | Honeywell Power Humidifier: Furnace...
Jul 08, 2008 | Goodman GMS90703BXA Heater
Aug 21, 2007 | Dometic Rooftop RV Air Conditioner
298 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: