Question about Goodman CLQ36AR49 Air Conditioner
Problem with excessive condensate driping from the coils and with the drain pan on the bottom of the unit my secondary drain connection is collecting water and tripping the flow switch shutting down the unit.
Go outside and find the drain outlet usually by the outdoor unit and **** it out with a shop vac , be sure its a wet dry vac. buy one if you dont have one. its cheaper than a service call do this twice a year.
Posted on Oct 11, 2008
The evaporator is probably not excessively condensing in as much as the amount of condensate is directly proportional to the amount of humidity in the air. It sounds like the problem is more likely the primary drain is restricted by algae; if this is the case I suggest pouring a cup of bleach in the primary drain and see if that clears the primary drain. Note: the secondary is just that it is designed to keep the water from overflowing into the house. Hope this helps!
Posted on Oct 05, 2008
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Aug 18, 2017 | Heating & Cooling
Jun 07, 2008 | Heating & Cooling
Sep 11, 2015 | Frigidaire Heating & Cooling
Aug 11, 2014 | Goodman Heating & Cooling
Feb 26, 2013 | Heating & Cooling
Feb 15, 2013 | Goodman Manufacturing Goodman GSC130181...
Oct 04, 2012 | Goodman CKL49AR49 Air Conditioner
Aug 05, 2011 | Goodman CLQ36AR49 Air Conditioner
Jul 13, 2011 | Goodman GMS90703BXA Heater
515 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: