Question about Ruud Heating & Cooling
Your unit sounds like it is short cycling on low pressure. find the cylindrical thing on the larger line in the unit.it will have two low voltage wires coming out of it. trace those two wires back to where they go and turn off the unit so you can install a jumper across them. turn on the unit and see if it keeps short cycling or if it is running more normal. if it runs more normal then you are most likely low on freon or a slight chance of an airflow restriction
Posted on Sep 22, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Aug 06, 2012 | Ruud UBHC Air Conditioner
Aug 21, 2011 | Ruud UBHC Air Conditioner
Aug 14, 2010 | Air Tools & Compressors
Jan 13, 2010 | Ruud Heating & Cooling
Sep 23, 2009 | Ruud UBHC Air Conditioner
Jun 11, 2009 | Ruud Matching Split Air Conditioner
May 28, 2008 | Ruud Matching Split Air Conditioner
Nov 20, 2007 | Heating & Cooling
Nov 20, 2007 | Ruud Central System Air Conditioner
102 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: