Question about Electrical Supplies
I have a 3 way switch with 1 light going into a room with another switch, 1 light at the bottom of the stairs and 1 light and 1 switch at the top of the stairs. and 1 main power cable gong in, and power to kitchen and up stairs bedrooms goes through this point. HELP
I have a light switch at the bottom of the stairs which works 2ways can be switched on and off up and down stairs and also an out side light on the same switch which I have messed up and would like a picture of the way it should be connected.
Posted on Oct 16, 2008
2 - three way switches are needed to operate a light or other things from 2 locations......first, all 3 ways have a 3 conductor cable that runs between them...colors are red, black and white......only one of the boxes requires power coming in from the panel on a 2 wire cable,,colors are black and white......the 3 way switches usually have one of the screws black and the other 2 screws are gold color.......the box that has only the 3 conductor cable going to it without the power cable can be wired directly to the switch....black wire to black screw, red and white wires to the gold screws.....the red and white wires don't matter to which of the gold screws you put them on.......the other box where there is also the power cable coming in is a little trickier..........i have an animation on my website that shows you how a 3 way system is wired if you like to check it out yourself....here is the address....www.freewebs.com/jselectronics........click on 'special services' at the top of the page and it will take you another page where you can see the animation....good luck
Posted on Jun 28, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Feb 27, 2015 | Electrical Supplies
Sep 26, 2012 | Gb Electrical GSW-117 Toggle Switch
Dec 22, 2010 | Leviton Decora Light Dimmer Switch
Dec 16, 2010 | Electrical Supplies
Sep 30, 2010 | Leviton Electrical Supplies
May 13, 2010 | GE Electrical Supplies
Mar 15, 2010 | APW Wyott C*Radiant, Lighted Double...
Feb 09, 2010 | Leviton COMBINATION SINGLE POLE TOGGLE...
Oct 01, 2009 | Cooper Wiring Devices 3-gang Cooper Wall...
Sep 23, 2008 | Leviton Decora Gray Rocker 4-Way AC Quiet...
1,144 people viewed this question
Usually answered in minutes!