Question about Honeywell Power Humidifier: Furnace Humidifier/ Humidifier
My Furnace does not shut off when the inside temp reaches the set degree. I have to use the emergency shut off to control the heat. Please help!
When I turn on my Oil Furnace after few minutes start smells to oil and then the smoke alarm on.
Posted on Jan 16, 2009
WEATHERKING OIL FURNACE FORCED HOT AIR SOMETIMES BURNER COMES ON AND IT DOESNT BLOW ANY AIR IT WILL JUST SHUT DOWN . MOST OF THE TIME IT WORKS GREAT WHAT COULD CAUSE THIS?
Posted on Dec 18, 2008
I am not a furnace guy but I may be able to give you a few ideas of things to diagnose the problem and get it resolved. First off, I assume you have a thermostat that you use to to turn your heat on. If it is a generic ( meaning : non programmable model) then you should be able to try this simple test. Remove the cover ( typically they snap on) around the thermostat so you can see the control mechanism inside. You should see few skinny wires ( similar to those used on a telephone wire) solid copper in various colors.. When you rotate the dial on your thermostat to call for heat, there is a small glass vial that has a drop of mercury ( which is electrically conductive) in it that makes contact and shorts two control wires together ad that is what calls for heat on your furnace. When the temp inside the room where the thermostat is reaches the tempertaure you requested, the bimetal mechanism either contracts or expands to reposition that glass vial to shift the mercury off the contacts and your furnace shuts off... That is the basics behind how your thermostat and furnace work ( generally speaking) If you can identify the two wires inside the thermosat that are shorted together when that vial of mercury shorts them inside it.. you can temproarily unhook them ( they are low voltage.. normally 24 Volts or less) so no worries about getting ashock or anything.. and short them together for a minute or two.. by doing that... your furnace should turn on and heat should flow.... Once you start your furnace this way.. unhook these two wires and your furnace should shut down .. It may take a minute or two ( depending on the control for it) If it doesn't..then your problem is on the furnace side and you may need to get the furnace control system serviced or replaced.. if it does shut down, then your problem is your thermostat and thats a simple replacement.. Also.. make sure the thermostat was properly leveled on its base.. The position of the thermostat ( meaning level) will dictate when that mercury makes contact and your furnace switches on.. OK..I tried to explain the works of this to you but here is a link to a Honeywell site that explains it in simpler terms.. The part about shorting the two wires together and then opening them will aid you in identifying where the problem actually is.. here is the link: http://homerepair.about.com/od/heatingcoolingrepair/ss/thermostat.htm
Hope this helps you more than confuses you..
Posted on Sep 20, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Oct 28, 2016 | Humidifiers
Jan 23, 2015 | Humidifiers
Nov 14, 2013 | Aprilaire 700 Humidifier
Jan 31, 2010 | Aprilaire 550 Humidifier
Sep 28, 2009 | Honeywell Power Humidifier: Furnace...
Jan 14, 2009 | Aprilaire 600 Humidifier
Jan 07, 2009 | Aprilaire 600 Humidifier
Jan 04, 2009 | Honeywell Power Humidifier: Furnace...
Nov 10, 2008 | Aprilaire 600 Humidifier
Dec 17, 2007 | Honeywell Power Humidifier: Furnace...
Dec 15, 2014 | Honeywell Power Humidifier: Furnace...
183 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: