Question about Carrier Heating & Cooling
Inddor Coil leaked and lost Puron resulting in no A/C function. Misdiagnosed 1st time and tech replaced 1 pound Puron. Not sure how much leaked out this time because system ran longer after knew A/C was not kicking in.
Doe entire Puron need to be drained and replaced with fresh/new product or can the lost amount just be replaced / charged?????
Carrier 38TDB037---30 / Indoor Coil FE4AN
Yup, entire system needs to be drained, and leak needs to be repaired first before charging with freon.
after sealing the leak and test it is ok, evacuate the system for about 30 mins before charging it.
you may need a qualified tech to do that because you can not buy freon now a days.
you need to weld the leak also. you will need portable torch to weld copper pipes.
you will need vacuum pump to evacuate the system before charging with freon 22.
tnx 4 using fixya,
Posted on Sep 18, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Apr 27, 2014 | Carrier Performance 2 Stage 17 Series 2.0...
Aug 31, 2010 | Carrier Heating & Cooling
Jul 18, 2009 | Heating & Cooling
Jun 28, 2009 | Carrier 38CKC030 Air Conditioner
Jun 10, 2009 | Heating & Cooling
Jun 09, 2009 | Whirlwind FH-778 Air Conditioner
May 09, 2009 | Carrier Heating & Cooling
Aug 01, 2008 | Carrier 38CKC036 Air Conditioner
May 19, 2008 | Heating & Cooling
275 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: