Question about Heating & Cooling
Listen to see if the contactors make a clicking noise when the fan starts to studder. If not, then it's not the signal to the contactors. If a clicking sound of the contactors can be heard, then the problem is the contactor coil dropping in and out. This could be a lose wire coming from the processor board, or a problem with the board itself. If no clicking is heard and the contactor is definitely not making and breaking the connection, then the problem could be a lose wire feeding power to the motor. This can be traced all the way back to where the power comes into the unit.
Posted on Sep 19, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Nov 03, 2015 | Heating & Cooling
Jun 05, 2011 | Heating & Cooling
Nov 16, 2010 | Mitsubishi Mr. Slim MXZ30TN Air...
Dec 29, 2009 | Intertherm P3RC-030K Air Conditioner
May 28, 2009 | Heating & Cooling
Feb 23, 2009 | Carrier Heating & Cooling
May 22, 2008 | Hitachi RAS-09UH Air Conditioner
501 people viewed this question
Usually answered in minutes!