Question about Intertherm P3RA-048K Air Conditioner
Wiring digram from ac to blower motor intertherm model FEHB-015HA
Posted on Apr 10, 2015
I need a wiring diagram for my furnace model#gmpn100-4 I can not find anything on this
Posted on Nov 12, 2008
A service rewired the because he didn't like the way it was wired from the factory, then they had a diffrent one to fix that. Now years later the blower motor burn out, another guy replaced it and messed up the blower to the blower relay
Posted on Oct 17, 2008
Why did the wiring burn?Id have the heat exchanger inspected before rewiring.better to be safe.
Posted on Sep 24, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Mar 14, 2014 | Goodman Heating & Cooling
Aug 16, 2011 | Heating & Cooling
You need to find out if the problem is in the T-stat, T-stat wire or in the furnace you can do this in a few easy steps
Step 1- Unwire the low voltage from the furnace. Then turn the power back on and see if the blower comes on if it does then the problem is in the furnace and you will need to troubleshoot the furnace (see bottom of page for troubleshooting furnace) if it does not then proceed to step 2
Step 2- Wire the low voltage back up to the furnace (follow the wiring diagram below). And unwire the T-stat, make sure that no wires are touching each other, then turn the power back on to the furnace, if the blower starts then you have a short in the T-stat wire and you will need to pull a new wire. If it does not then proceed to step 3
Step 3- Turn the power back off at the furnace and wire the T-stat back up (follow the wiring diagram below). Turn the T-stat to auto heat 90 if the heat does not start but the blower just runs then you need to replace the T-stat.
Nov 24, 2010 | Comfort-Aire Heating & Cooling
Mar 29, 2010 | LG LWHD1800R Wall/Window Air Conditioner
Oct 13, 2009 | Heating & Cooling
Jul 11, 2009 | Heating & Cooling
Jul 08, 2009 | Dometic Rooftop RV Air Conditioner
Apr 28, 2009 | Heating & Cooling
Jun 14, 2008 | Ruud UBHC Air Conditioner
394 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: