A new zoneline AZ29 was instaled yesterday. It is turning on by itself with tno lights in the panel . When I turned it off it keeps on running. I liv ein PR and won't need the heat functions.
I want to be able to turn the air on/off manually
The GE Zoneline units have small DIP switches inside the unit where you can turn various functions on or off. The units have a feature called Heat Sentinel that turns the A/C on at a certain room temperature, even when the unit is turned off. It also has a Freeze Sentinel that turns the heat on automatically, even when the unit is turned off. You can turn off the heat and freeze Sentinel features with the DIP switches in the unit. There are other features you may want to turn off. Read the owner's manual and it will tell you where the switches are and which ones turn off the features. Hope this helps.
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US. click here to Talk to a Repairman (only for users in the US for now) and get all the help you need. Goodluck!
- If you need clarification, ask it in the comment box above.
- Better answers use proper spelling and grammar.
- Provide details, support with references or personal experience.
Tell us some more! Your answer needs to include more details to help people.You can't post answers that contain an email address.Please enter a valid email address.The email address entered is already associated to an account.Login to postPlease use English characters only.
Tip: The max point reward for answering a question is 15.
I worked extensively on GE Zoneline AZ Air Conditioners and Heat Pumps while a Maintenance Superintendent at a Senior Citizen's Apartment Complex. Not knowing what type of smell to which you are referring, I can assure you that other than "burnt electrical" smells, the only smell that could possibly be produced would be that from within the INDOOR SPACE. Perhaps something has made its way into the INDOOR AIR FILTER? Perhaps that INDOOR AIR FILTER needs to be cleaned. To clean the INDOOR AIR FILTER, simply lift both of the filters from the front cover, take to your clean bath tub. Run EXTREMELY HOT WATER from the back of the filter to the front of the filter. Then, fill your bathtub 1/4 way with EXTREMELY HOT WATER. Add 1 cup of Hydrogen Peroxide and 1 cup of Real Lemon Juice. Set both filters in this solution for 30 minutes; then rinse with clear water. Set filters up to dry for at least 2 hours in the sun or an air breeze. Replace filters into the GE Zoneline.
Also, not knowing how OLD your GE Zoneline system is, the COILS may need to be cleaned. To do this, simply turn OFF your GE Zoneline unit and remove the front COVER of the unit. Next, mix in a spray bottle 4 packets of LEMON flavored KOOL-AID (without SUGAR) and water. Shake well. Spray the INDOOR COILS of your GE Zoneline unit with the entire contents of this mixture. Let set for at least 10 minutes. Then turn your GE Zoneline to the COOL position. The citric acid in the lemon kool-aid will be forced through the coils to continue to remove any dirt, dust, debris and effectively CLEAN those coils. This will also provide you a LEMONLY odor within your room. Simple and cheap.
My name is brian pfeiffer . I run a ptac business in griffin ga. I have many parts and filters for most all types of ptac units. Please feel free to contact me at email@example.com. Nobody can beat my prices!!!! Or call me at 770-233-9987
One might think so, YES the compressor is running till it gets hot and tripps on hi-temperature, and after it cools down awhile, the switch willcautomatically reset itself and back- & forth......Thank-you-very much!
well this is a very subjective question. How mechanically adept are you. If you know where to find the replacement OEM part, then its a mater of taking the control panel apart and replacing the wires one at a time from the old thermostat to the new one. It will have a sensor probe that will need to be routed and attached to the coil somewhere. The same place as the old one. make sure the bulb (if it has one) is not damaged. This may go without saying, but make sure the power is off first.