Question about Amana PTH123B25AJ Heat Pump Air Conditioner
Verify that the contactor rely is closing. if not possible low or high pressure switch has tripped. some are push button resetable some not. does the outdoor fan run?
Posted on Nov 22, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
My parts lookup too has no images available for you refrig but i believe it to be a GE Profile with a fresh food fan (and air duct down the center of the fresh food side). All fan motors are 12vdc and run off the Lowvoltage side of motherboard. i assume you are checking voltage to comp from motherboard? How did you check relay?? Have you axcessed motherboard?? On the top of (I say top-- i belive its mounted horiz on yours but all the small wires are on the right) is all the low voltage fan motor, damper, control wiring On the bottom (or the left) side of the motherboard is the larger line voltage wiring. The connector with 3 wires is labeled def -- comp---line it should be blue. Try jumping L1 to comp. ((Just so ya know Def will energize the def heater regardless of compartment temp it does have a bimetal but it only a safety set at 100deg in case relay on board welds shut---it monitor evap compartment, frz, fresh food, (two seperate in FF) in your model))
Oct 11, 2007 | GE PSI23MGN Side by Side Refrigerator
I just had the same problem. I replaced the motor with no luck. It turned out to be a bad capacitor. If it is a dual capacitor, three prongs on top, it also starts the compressor. It is recommended to replace the capacitor anytime you replace a motor. I would try replacing the capacitor first. It is a lot cheaper that a new motor. If that does not fix the problem then you can get a motor. No harm, no foul. The slow start of the motor is a common symptom of a bad capacitor. The motor is not getting enough voltage. The capacitor increases the voltage like a transformer. It will boost it to almost 400 volts, depending on your unit.
Jun 21, 2012 | Heating & Cooling
May 16, 2011 | Weather King 10AJA6001AH Air Conditioner
Jan 16, 2010 | Heating & Cooling
Jun 13, 2009 | Kenmore 54701 Dehumidifier
Sep 14, 2017 | Samsung Televison & Video
Feb 04, 2009 | eMachines T6534 PC Desktop
Jan 25, 2009 | eMachines T6534 PC Desktop
Feb 02, 2016 | Amana PTH123B25AJ Heat Pump Air...
46 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: