Question about Carrier Heating & Cooling
You will need to cut off power
find the gas shut off at your unit and cut off.
Loosen the fitting after the cut off and open the cut off slowly until you smell gas. re tighten and turn gas and power back on.
Posted on Nov 29, 2008
I assume this is a manufactured home, this is probably a two transformer system, either your contactor is welded in the on positon or wyou have control wiring issues, (could be the thermostat)
Posted on Jul 12, 2009
Sounds like some of the elements are not working. You being in Florida they may not have put very many elements in. It was 61 degrees last week. I know because I'm a Dolphin Fan. You will need a current sensing meter to check the elements.
Posted on Jan 04, 2010
Testimonial: "Perfect... The problem was with the Defrost control unit... apparently the outdoor unit was icing up every night, defrost control element was bad!"
Tips for a great answer:
Feb 03, 2017 | Honeywell Heating & Cooling
Jan 26, 2016 | Heating & Cooling
Nov 22, 2015 | Heating & Cooling
Dec 14, 2013 | Honeywell Programmable Thermostat Heater
Sep 04, 2012 | Goodman GMS90703BXA Heater
Feb 10, 2010 | Heating & Cooling
Oct 02, 2009 | Dayton Gas Furnace Heater
Jul 11, 2009 | Dayton Gas Furnace Heater
Jan 12, 2009 | Heating & Cooling
41 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: