Question about Heating & Cooling
It blows hot air when it's supposed to be cooling off.
Verify if you have separate units for each floor.
the ones working could be a complete separate unit from the one having problem.
look at the condensing units you got outside , how many are there?
if you have 3 units outside and you have 3 thermostats, then each thermostat is controlling individual split units.
we have to concentrate on the one that is not cooling. give me the details on what is going on with problematic one.
is the outside unit running?
is the outside fan running?
can you distinguished if the compressor is running the same time as the fan?
tnx 4 using fixya,
Posted on Sep 14, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Sep 19, 2015 | Robertshaw Thermostat Accessories 9010-1...
Jan 27, 2015 | 2002 Pontiac Grand Am
Jan 16, 2015 | Robertshaw 9600 Heat / Cool Digital...
Jan 11, 2015 | Robertshaw 9600 Heat / Cool Digital...
Oct 06, 2010 | Heating & Cooling
Feb 04, 2010 | Shaw Robert RS-9420 Thermostat
Jan 08, 2010 | Heating & Cooling
Jul 25, 2009 | Shaw Robert RS-9420 Thermostat
Jun 02, 2009 | Honeywell Programmable Thermostat Heater
Jan 16, 2009 | Heating & Cooling
Feb 26, 2017 | Heating & Cooling
625 people viewed this question
Usually answered in minutes!