Question about Heating & Cooling
First question first, NO! this is a simple problem and a common one to fix, just change out the outside contactor coil, the contactor has a thin layer of silver on them to prevent them from arching and sticking together, over time this thin layer burns through and stick the contactor and wont let go, till you replace the contactor coil,(20.00) 24-volt 40 voltage amp coil! YOU CAN DO THIS after you kill the power to the unit.!Thank-you-very-much!
Posted on Sep 13, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jul 11, 2014 | Maytag Portable Air Conditioner M6P09S2A
Feb 05, 2014 | Goodman Manufacturing Goodman GPH1348H41...
Sep 27, 2012 | Goodman Manufacturing Goodman GSC130301...
Jun 11, 2011 | Carrier 38CKC036 Air Conditioner
May 28, 2010 | Dometic Rooftop RV Air Conditioner
Jul 06, 2009 | Heating & Cooling
Jun 16, 2009 | Heating & Cooling
Jun 06, 2009 | Goodman CKL42AR42 Air Conditioner
Mar 15, 2009 | Samsung AW0693L Air Conditioner
Jul 22, 2008 | Heating & Cooling
142 people viewed this question
Usually answered in minutes!