Question about Smith A. O. Single Speed J-Frame Threaded Shaft Full-Rated Motors for Hayward Northstar Pumps - 1 HP
My idea is to design circuit to automatic shut down pump when pump loses vacuum.. So far I have contactor either with 24 coil or 110v coil in series with vacuum switch.My problem is circuit will not close upon time clock starting pump because vacuum switch has no vacuum.If I could temporary short vacuum switch with time delay it would than be able to shut pump down if it lost vacuum for some reason. Any ideas
A momentary contact switch can be used to bypass the vacuum switch until operating pressures and vacuums are reached. It is called a start switch.
Posted on May 04, 2009
You need to install a time delay relay.
Posted on Nov 08, 2008
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jun 27, 2012 | Goodman Heating & Cooling
on Aug 21, 2010 | Heating & Cooling
Mar 26, 2012 | Heating & Cooling
Aug 20, 2011 | Friedrich Heating & Cooling
Jul 14, 2011 | Heating & Cooling
Dec 12, 2010 | Heating & Cooling
May 05, 2010 | Intertherm P3RA-060K Air Conditioner
Jun 06, 2009 | Plumbing
Apr 30, 2009 | Ruud Central System Air Conditioner
Jul 20, 2008 | Ruud Heating & Cooling
140 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: