Question about Heating & Cooling
These furnaces goes thru 4--steps for complete run time.... step-1, the small draft inducer blower motor blows and prove thru the small air tube that sucks a switch close to tell the circuit board to go to step-2......the glow plug glows for 15 seconds and step 3 the gas valve opens and dump gas in the venturi tubes and lights off the glow plug and proves thru a flame sensor (pin with 1 electrical wire connection) on the last venturi tube which tells the circuit board to go to the last step 4--, to turn on the main blower fan after 90 seconds!. Where ever it stops at then thats where your problem is!
Posted on Sep 13, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Oct 25, 2012 | Intertherm 56000 Btu Gas Furnace
Jan 08, 2011 | Coleman Heating & Cooling
Mar 08, 2010 | Heating & Cooling
Jan 10, 2010 | Armstrong H 67 1PH Bf In Line Circulator...
Nov 28, 2009 | Heating & Cooling
Oct 12, 2009 | Goodman GMS90703BXA Heater
Feb 11, 2009 | Ruud Central System Air Conditioner
Nov 27, 2008 | Aprilaire 700 Humidifier
Nov 23, 2008 | Heating & Cooling
258 people viewed this question
Usually answered in minutes!