Question about Air Conditioners
These furnaces goes thru 4--steps for complete run time.... step-1, the small draft inducer blower motor blows and prove thru the small air tube that sucks a switch close to tell the circuit board to go to step-2......the glow plug glows for 15 seconds and step 3 the gas valve opens and dump gas in the venturi tubes and lights off the glow plug and proves thru a flame sensor (pin with 1 electrical wire connection) on the last venturi tube which tells the circuit board to go to the last step 4--, to turn on the main blower fan after 90 seconds!. Where ever it stops at then thats where your problem is!
Posted on Sep 13, 2008
Tips for a great answer:
Jan 08, 2011 | Air Conditioners
Dec 26, 2010 | Goodman CACF048B2A Air Conditioner
Mar 08, 2010 | Air Conditioners
Mar 10, 2009 | Air Conditioners
Feb 11, 2009 | Ruud Central System Air Conditioner
Dec 21, 2008 | Air Conditioners
Nov 23, 2008 | Air Conditioners
257 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: