Question about Goodman Heating & Cooling
Clicking sound is the contactor engaging to start the outside unit. Check for a burnt off wire at the contactor. For some reason you are not getting power to the outside unit. If you find a burnt off wire shut off all power to it then remake the connection at the point of the circuit break.
Posted on Jun 27, 2008
Tips for a great answer:
Feb 22, 2015 | Goodman Heating & Cooling
May 21, 2014 | Goodman 3 Ton 14 ee Goodan Heat Pump...
Jan 23, 2013 | Goodman Manufacturing GPG1342090M41...
Jul 21, 2011 | Goodman Heating & Cooling
May 20, 2010 | Goodman CLQ36AR49 Air Conditioner
Mar 05, 2010 | Goodman CKL60AR60 Air Conditioner
Dec 24, 2009 | Goodman CKL24AR24 Air Conditioner
Jul 17, 2009 | Goodman CKL36AR36 Air Conditioner
Feb 16, 2009 | Goodman PHKJ048-1 Air Conditioner
Jun 26, 2008 | Goodman CKL60AR60 Air Conditioner
55 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: