Question about Ruud UBHC Air Conditioner
My air conditioner is about 12 years old. problem is that the unit has not stopped running since yesterday. the air flow is still cool, but i did notice that the pipe that releases any water is dry. Help
Possibly two or more problems. drain may be plugged and therefore no water dripping from it. attach a good wet dry shop vac and **** it out. listen for good suction at in door coil when vac is attached outside . feel large insulated line outside . it should be ice cold to touch but not frozen . if it is kinda cool then your low on gas. if its froze you are low on gas or dirty filter ,coil , or blower wheel. .you can measure temp drop between return air in and supply air out at the in door blower . it is usually 18 to 20 dgrees , in at 80, out at 60 so to speak. greater than 2o and you have a restriction like dirty or filter or froze up. less than 15 you are low on gas or inefficient compressor. be sure your fan is in the auto mode , not the on mode or indoor fan will run 24-7.
Posted on Oct 24, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Aug 20, 2012 | Heating & Cooling
Jan 13, 2010 | Heating & Cooling
Sep 09, 2009 | Ruud Heating & Cooling
Jul 29, 2009 | Movincool Office Pro 12 Air Conditioner
Jun 28, 2009 | Amana PTH123B25AJ Heat Pump Air...
Jun 25, 2009 | Heating & Cooling
Mar 27, 2007 | LG LWHD1800R Wall/Window Air Conditioner
93 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: