Question about Goodman Air Conditioners
When this happens, most often you'll have a stuck contactor coil on the condenser. If you buy it , it should cost $20---to 15.00 and you can add if you turn off the power (240volts) and the furnace power!
Posted on Sep 09, 2008
Tips for a great answer:
Sep 24, 2014 | Air Conditioners
Apr 16, 2013 | Goodman Air Conditioners
Jan 17, 2013 | Gibson Air Conditioners
Jul 18, 2012 | Goodman Air Conditioners
Sep 07, 2011 | Air Conditioners
Jun 28, 2011 | Goodman CKL36AR36 Air Conditioner
May 19, 2011 | Air Conditioners
Sep 08, 2010 | Air Conditioners
Sep 29, 2008 | Carrier 38BRC048 Air Conditioner
54 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: