Question about Heating & Cooling
Is this a central unit or a window unit. The central unit does 15*----18 * temperature difference from the air comming in the return air grill to the air going out the supply air grills...9*----to ----14* degree different, and the unit is low on freon,, 15*--18* and the charge of freon is perfect, 19-----22* difference, then the air flow is too low , due to either a dirty filter,, dirty squirell cage blower wheel, and last , but not least, the ac inside coil is plugging up!
Posted on Sep 07, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Dec 28, 2016 | Heating & Cooling
Aug 24, 2014 | Honeywell Th5220d1003 Non-programmable...
Jul 21, 2011 | Sunbeam Heating & Cooling
Feb 09, 2011 | Heating & Cooling
Dec 27, 2010 | Dayton G73 Utility Heater
Dec 27, 2010 | Honeywell CT500 Digital Heat / Cool Manual...
Dec 19, 2010 | Goodman PHKJ024-1 Air Conditioner
Jun 23, 2009 | Honeywell Programmable Thermostat Heater
Jun 19, 2009 | Honeywell Programmable Thermostat Heater
Aug 22, 2008 | Whirlpool Heating & Cooling
133 people viewed this question
Usually answered in minutes!