Question about Haier Energy Star ESA3183 Air Conditioner
The heat pump in my air conditioning system trips the circuit breaker... what do I do?
Posted by Anonymous on
I want to know the size of breaker to use.we are using a 30,30,30,30but it is kicking off.would a 40,40,40,40or higher be better if they sell them.
Posted on Nov 22, 2008
I seem to have the same problem. But when I reset the breakers, they won't stay in the on position. They go back to the off position. What gives? It is 95F inside the house.
Posted on Jul 22, 2008
The breaker for the air handler may be to small for the heat strip. Check to see the size of your heat strip (KW) and make sure that you have the right size breaker for the heat strip.
Posted on Jan 15, 2008
Most heat pumps have auxiliary heating elements that provide heat when the weather gets really cold because the heat pump's efficiency drops too low. These elements automatically turn on at a fairly low temperature: around 20 degree F. When they come on, they may be drawing too much power, which trips the circuit breakers. Just locate the circuit breaker that serves the heat pump and reset it.
Posted on Jan 18, 2006
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
the start capacitor is bad. Motors develop what is known as lock rotor amperage. requires alot of torque to turn the motor until it reaches iits rated or run load amperage. the motor is not able to overcome the lock rotor amps which is usually 5x the rated amperage and always more amps than the breaker. this is usually not a problem because the start capacitor helps overcome the LRA so quickly that it doesnt trip the breaker. If the capacitor is round and bad it will be bulged at the top, if it is oval shaped then the rupture disc on top will be blown letting all the dielectric fluid out which cools the capacitor
Posted on Dec 15, 2009
Tips for a great answer:
Jul 25, 2016 | Celiera Celi 24000 BTU Ductless Mini Split...
Apr 14, 2015 | Heating & Cooling
May 16, 2014 | Goodman CLQ36AR49 Air Conditioner
Mar 08, 2013 | Heating & Cooling
Sep 10, 2011 | Heating & Cooling
Jul 19, 2010 | Challenger Connecticut Electric UBITB-A230...
Jan 29, 2010 | Heating & Cooling
Aug 01, 2009 | Amana PTH123B25AJ Heat Pump Air...
Oct 22, 2008 | Haier Energy Star ESA3183 Air Conditioner
1,879 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: