Question about Haier Energy Star ESA3183 Air Conditioner
The central air conditioner in our house doesn't cool.. any help would be appreciated.
Posted by Anonymous on
A central air conditioner that runs but doesn't cool may just need to be cleaned. Plan to do this on a relatively warm day. First look for your owner's manual and, if you can find it, follow its instructions. If you can't find it, request one from the manufacturer (see Resources). To clean the filter, remove it from the furnace or air handler (it?s usually located inside or very near the air inlet side). Replace a disposable filter or clean a reusable filter according to the manufacturer?s directions. 1) Before you begin, check the thermostat to make sure it is set to "cool" rather than "heat." Then turn off the power to the unit; there is normally a shut-off or disconnect panel on the house wall next to the outdoor compressor. Otherwise, shut off the air conditioner's 240-volt circuit at the main electrical panel. 2) Rake leaves and debris away from the outdoor condenser. 3) Remove any protective grille or cover from the condenser's fins. 4) Use a soft brush to clean dirt and debris from the fins, then vacuum them with a brush attachment (be careful not to bend or damage them). If you accidentally bend fins, you can buy a comb made for straightening them at an appliance parts store. 5) Unscrew and lift the top grille off the unit, if possible. If the fan is attached to the grille, be careful not to pull any wires loose. 6) From inside the unit, hose out the fins (protect the wiring and motor with plastic). If your owner's manual calls for lubricating the motor, do that now--don't over-lubricate. 7) Then reassemble the unit. 8) To test it, turn the power on and set the thermostat to turn the unit on. Let it run for a few minutes, then feel the two pipes that connect to the condenser unit (slide any insulation back). One should feel warm, the other cool. Otherwise, call an air conditioning technician--the refrigerant may need to be recharged. NOTE: Avoid straining an air conditioner's compressor by waiting at least five minutes between turning it off at the thermostat and turning it back on. Air conditioner or heat pump still giving you trouble? To Home Problem Solver Main Page Copyright. All rights reserved. Interested in licensing this DIY Content? Related terms: what to do if, how to fix, troubleshooting, DIY, air conditioner doesn't cool, air conditioner too warm, warm air from air conditioner, air conditioner not cold enough, how to clean air conditioner, cleaning air conditioner, air conditioner cleaning
Posted on Jan 18, 2006
Usually when a unit isn't cooling it is because one there isn't enough freon in the unit. Second there could be a compressor gone bad. Third there could be a circuit short out. It can be very simple and it can be costly. It just needs to be checked out by someone who has understanding in this area.Look for an affordable service man or company in your area whom most people may be using to come out and check it out for you. They would be glad to. They can let you know about what it might cost also. If you have understanding in this area you might do it yourself. I do most everything myself and it keeps alot of money in my wallet. But I have to take the time to do it.
Posted on Aug 08, 2007
If both the indoor furnace (or air handler) and the outdoor condenser are running then you should call a service company. If one or the other is not working then turn the breakers for them off and then back on. This might just work. Good luck.
Posted on Jun 15, 2008
Most likely, it is out of freon, the fluid that transfers heat and cold in the unit. You should call an A/C tech to have him look at it.
Posted on Aug 08, 2008
Check the circuit breaker; it may just need to be reset. That's what worked for me: the fan would run but wouldn't cool and turns out the fuse had tripped. A reset fixed it.
Posted on Oct 21, 2007
Thanks for your question!
I'm sorry that you haven't received an answer yet.
The response rate on FixYa FREE questions is usually over 80%, but sometimes questions go un-answered when:
1. the question is unclear, incomplete, or poorly worded...
2. the question is mis-categorized - so the correct experts aren't viewing it...
3. the question requires an answer for something that cannot be explained online adequately...
4. specific training, tools, or equipment are required to avoid injury or death...
5. the Experts that are online simply don't have the resources to answer your question fully...
Please feel free to re-work your question if you feel one of these may be the reason.
Of course you are not required - but converting your question to a PAID one usually increases the reply rate as well.
Normal rates for FixYa are...
$ 9.99 answer for one question.
$12.99 Live Real-Time online chat or premium e-mail support.
$29.99 Live Real Time phone support
Sometimes FixYa will run specials for unlimited questions via monthly subscription or reduced rates for limited periods.
Consider the savings that can be had when an informed Expert can save you a $100 service call, or a $350 trip to the car dealership.
Your problem solved - guaranteed! Or your money back!!
If you don't want to pay - feel free to re-submit your question so it returns back to the top of the work queue if you still need help.
Thanks for using FixYa - a 4 THUMBS rating is appreciated for helping with your FREE question
Posted on Sep 04, 2010
Tips for a great answer:
Apr 22, 2012 | Air Conditioners
Oct 05, 2011 | Frigidaire FAH125P2T Air Conditioner
Sep 03, 2011 | Fedders A&B Chassis A1A07W2B Air...
Jun 23, 2011 | LG Heat cool Window Air Conditioner
Dec 13, 2010 | Haier HC48C1VAR Central Air Conditioner
Aug 09, 2009 | Carrier Air Conditioners
May 21, 2009 | Carrier Air Conditioners
Jun 14, 2008 | Kenmore 72055 Air Conditioner
Jul 01, 2014 | Haier Energy Star ESA3183 Air Conditioner
7,291 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: