Question about Amana Heating & Cooling
This unit goes in steps, 1-- thru--4 Step 1, vent fan blower motor runs & prove thru the air tube, which closes a switch and tells the circuit board to go to step---2 Step 2 lights the glow plug and goes to step 3 automatically, Step 3, opens the gas valve and send in gas thru the long venturi tubes which lights from the glow plug and on the last tube, theres a rod that sticks into the flame, if no flame or not working properly, it will shut down the starting sequences and retry for 4-times and automaticaly lockout till unplug and start over. (whever step it stops at, then thats where your problem is!
Posted on Sep 06, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Apr 19, 2011 | Amana Heating & Cooling
Mar 07, 2011 | Amana Heating & Cooling
Dec 05, 2010 | Heating & Cooling
Nov 28, 2010 | Heating & Cooling
Nov 02, 2008 | Amana Heating & Cooling
697 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: