Question about Maytag Kitchen Ranges
Proper air velocity over the burner is critical on a direct fired gas unit. If the air velocity is not within
specifications, the unit will not operate efficiently, can produce excess carbon monoxide (CO) or other gases, and may have sporadic shutdowns. Proper air velocity is determined by measuring the static pressure drop across the burner.
To measure the static pressure drop, the fan should be running and be discharging 70° air. Using an incline manometer or equivalent, insert one sensor into the entering air access opening (plugged test port) and the other on the downstream side, through the view port (see page 12 for locations). The proper static pressure reading should be from .625 in. to .675 in.
If this reading is higher or lower and the air quantity (cfm) delivered to the building is acceptable, then the burner baffles will need to be adjusted (see diagram).
Open the burner access door. Using a wrench loosen the 4 screws to adjust the baffles. To increase the static pressure loss, decrease the opening size and to decrease the loss, increase the opening size. The top and bottom baffles should be of equal distance from the burner. Tighten the baffle fasteners, replace the door, turn unit on, and recheck the loss. This process may need to be repeated
until the proper pressure reading is attained.
This adjustment will change the air quantity delivered by the unit and therefore should be rechecked.
Posted on Sep 05, 2008
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Feb 02, 2016 | Kitchen Ranges
Jul 06, 2017 | Kitchen Ranges
Jul 05, 2012 | DCS RGS-486GL Stainless Steel Gas Kitchen...
Apr 23, 2012 | Stoves Kitchen Ranges
Oct 29, 2010 | Wolf Range CHR-0-29-FT34 Gas Kitchen Range
Jul 23, 2009 | Kitchen Ranges
Jul 18, 2008 | Jenn-Air JGR8855BDS Gas Kitchen Range
May 23, 2008 | GE Profile Spectra JGBP90 Gas Kitchen...
686 people viewed this question
Usually answered in minutes!