Question about GE Zoneline Deluxe Series Cooling & Electric Heat Unit AZ25E07D3B
Check the back coil from the inside and see if they are plugged up, where the fan blades throws the water and air on the back coils ( If this is plugged solid and can,t get rid of heat, the Iamps wll climb and tripp out the overloads, and will restart later on when it cools down and continue to trip this cycles till the overloads burnout! Thank You very much!
Posted on Nov 05, 2008
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 24, 2018 | Generac Electrical Supplies
Jan 11, 2018 | Inverter Electronics - Others
Dec 05, 2013 | Northstar North Star Honda 13hp 8000 Ppg...
Feb 06, 2013 | 1993 Dodge Dakota
Oct 16, 2012 | Computers & Internet
Sep 06, 2011 | Coleman Powermate Powermate 5000W...
Aug 27, 2011 | Amana Heating & Cooling
Dec 27, 2010 | Ingersoll Rand 2340/2475 Electric Air...
Dec 06, 2010 | Heating & Cooling
Nov 24, 2009 | Fahrenheat Ceiling-Mount Industrial Heater...
57 people viewed this question
Usually answered in minutes!