Question about GE Zoneline Deluxe Series Cooling & Electric Heat Unit AZ25E07D3B
Check the back coil from the inside and see if they are plugged up, where the fan blades throws the water and air on the back coils ( If this is plugged solid and can,t get rid of heat, the Iamps wll climb and tripp out the overloads, and will restart later on when it cools down and continue to trip this cycles till the overloads burnout! Thank You very much!
Posted on Nov 05, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Apr 04, 2016 | Heating & Cooling
Jun 21, 2015 | Dometic Heating & Cooling
Aug 27, 2011 | Amana Heating & Cooling
Jul 12, 2011 | Weather King Heating & Cooling
Jun 08, 2011 | Royal Sovereign Heating & Cooling
Mar 30, 2011 | Heating & Cooling
Dec 06, 2010 | Heating & Cooling
Feb 05, 2010 | Goodman PHKJ048-1 Air Conditioner
Aug 27, 2009 | Coleman Mach III Air Conditioner
Jun 21, 2009 | Goodman CLQ36AR49 Air Conditioner
56 people viewed this question
Usually answered in minutes!