Question about Heating & Cooling
Furnace has been serviced regularly each year. Ran fine last winter, air worked fine all summer when needed. When I turned thermostat to heat and dial up to call for heat the inducer fan starts and the ignition lights the pilot, but the burners will not kick on. Oh, I should correct myself. Last winter, 1 time the burners would not light for a few hours and when I shut off the power and checked everything I could (connections, etc..), I turned the power back on and it worked fine the rest of the winter. Any thoughts?
There are 4 -steps for full run time to kick in a furnace.. step-1, inducer fan runs & prove thru the air tube which closes a switch and tell the circuit board to go to step-2, the igniter lights the pilot & prove its lit by heating the thermocouple, which tells the circuit board to go to step-3, opens the gas valve to dump gas in, which will light from the pilot light, and prove by a flame sensor metal stick on the last burner , which heats up and tell the circuit board Saying, ok , I've got flame.. step-4. when the box heats up, it closes a switch and turn on the main fan...! (Some gas-valves has a brain -or circuit board on top of them and are real sensetive to moisture..)
Posted on Sep 05, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Nov 08, 2011 | Carrier XHB123D X/Y Series Heat/Cool Air...
Sep 22, 2010 | Heating & Cooling
Nov 15, 2009 | Carrier XHB123D X/Y Series Heat/Cool Air...
Jan 25, 2009 | Carrier XHB123D X/Y Series Heat/Cool Air...
Dec 30, 2008 | Heating & Cooling
Oct 22, 2008 | Carrier XHB123D X/Y Series Heat/Cool Air...
Oct 17, 2008 | Carrier XHB123D X/Y Series Heat/Cool Air...
Dec 17, 2007 | Heating & Cooling
287 people viewed this question
Usually answered in minutes!