Question about Heating & Cooling
For the correct temperature change, the different temperature should be at least 15*--20* degree temp. change from the air sucking in in front of the filter, and from the air blowing out of the front unit. use a thermometer!IIf, not, then you have 2- choices, low on freon, or a dirty ,back coil where the fan blades are.!
Posted on Sep 05, 2008
"Too much is just as bad as not enough!" FREON that is. have you had someone add freon to this unit?
Posted on Sep 04, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jun 23, 2015 | Norpole 5000BTU Mechanical Window Air...
Sep 06, 2013 | Goodman PHKJ048-1 Air Conditioner
Jul 14, 2011 | Ruud Matching Split Air Conditioner
Apr 04, 2011 | Heating & Cooling
Aug 23, 2010 | Heating & Cooling
Jul 30, 2010 | Ruud UBHC Air Conditioner
Jul 03, 2009 | Goldstar M5200R Air Conditioner
Sep 01, 2008 | Ruud UBHC Air Conditioner
Sep 19, 2007 | Carrier 38CKC042 Air Conditioner
100 people viewed this question
Usually answered in minutes!