Question about Honeywell Heating & Cooling
R==power w=heat y=cool g=fan remove the front cover to reveal the 4-wires and take a jumper wire from r-----to ---g ,to see if the fan operates. Then take the jumper wire from r----to--y, to see if the cooling system works outside, because when calling for cool, the thermostat is internaly connected to g--for fan.. Then if it kicks in, then you have a bad thermostat!
Posted on Sep 04, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Oct 28, 2016 | Honeywell PRO 3000 Non-Programmable...
Jun 04, 2016 | Honeywell TH5110D1006 Focus PRO 5000...
Jan 05, 2016 | Computers & Internet
Jul 25, 2014 | Honeywell Focus Pro 6000 Programmable...
May 14, 2014 | Honeywell Thermostat Pro 3000 Th3110d1008
Sep 14, 2010 | Honeywell Programmable Thermostat Heater
Oct 25, 2009 | Honeywell Electronic Programmable...
May 16, 2009 | Heating & Cooling
Sep 30, 2008 | Heating & Cooling
295 people viewed this question
Usually answered in minutes!