Question about Goodman CKL60AR60 Air Conditioner
A couple of issues here.......... 1) 29 sounds more like amps and not Volts. 2) if the amps are high at 29 amps that generally indicates that the compressor may be overloaded. There are several reasons for overloading of the compressor. It could be overcharged, this is common from fly by night AC repairmen they take advantage of consumers because there is not really a good way for the customer to know what the refrigerant levels/temps/pressures should be. Another potential problem is a dirty condensor not allowing the refirgerant to cool and condense in the outside unit. Lastly the inside unit could be dirty causing freezing conditions in the evaporator (inside unit) thus causing the compressor to work harder inturn causing more amps...... Now with all that said, the compressor has no impact on over VOLTAGE, this is something that is controled by the local power company... Hope this helps....
Posted on Oct 03, 2008
Get a second opinion from a different company
Posted on Sep 03, 2008
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Nov 13, 2017 | Televison & Video
Feb 26, 2013 | Heating & Cooling
Jul 11, 2010 | Whirlwind FH-778 Air Conditioner
Jul 06, 2010 | Weather King 10AJA6001AH Air Conditioner
Jul 22, 2009 | Ruud UAKA042 Air Conditioner
Jun 15, 2009 | Ruud Handle Air Conditioner
May 04, 2009 | Amana ABB2224DEW / ABB2224DEQ / ABB2224DEB...
Oct 04, 2008 | Air Tools & Compressors
Aug 18, 2008 | Heating & Cooling
113 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: